Expansion valves are devices used to control the refrigerant flow in a refrigeration system. They help to facilitate the change of higher pressure of liquid refrigerant in the condensing unit to lower pressure gas refrigerant in the evaporator. This article will take a closer look at a common type of valve called the automatic expansion valves. This guide will help you understand what is automatic expansion valve and its function.
The automated expansion valve (AXV) is similar to the thermostatic expansion valve (TXV) in terms of manufacture and appearance. The Automatic Expansion Valve Is an Important Product to Use in Industrial Applications and Plumbing Systems. Automatic Expansion Valves are provided by several Suppliers and Companies, different manufacturers, and a lot of distributors and there are a lot of Automatic Expansion Valves for Sale on Linquip.
There is a complete list of Expansion Valve services on the Linquip website that covers all of your needs. Linquip can connect you with a number of different industrial Expansion Valve service suppliers. Linquip offers a team of Expansion Valve Specialists ready to help you test your equipment.
Read on this new blog in Linquip to find out more.
⇒ View a Comprehensive List of Valves and Their Suppliers ⇐
What is an Automatic Expansion Valve?
Automatic expansion valves or constant pressure expansion valves are a type of valve used to regulate a refrigerant’s pressure in a cooling or refrigeration unit. It helps meter liquid refrigerant to the evaporator, ensuring that the pressure is where it needs to be to achieve the state change from liquid to gas. The automatic expansion valve maintains constant pressure inside the evaporator no matter what the load inside the evaporator is.
Automatic Expansion Valve Construction
The automatic expansion valve consists of the metallic body inside which is the metallic diaphragm or bellow. On the upper side of the diaphragm is the spring which is under pressure and its pressure is controlled by the adjusting screw.
Below the diaphragm, there is a thin plate or seat that has a small opening. The opening in the seat is controlled by the needle or stem connected to the diaphragm. As the diaphragm moves down the needle also moves down thus opening the valve. The seat and the needle form the orifice for the constant pressure valve.
There are also two openings in the valve. From one side, the refrigerant from condenser enters the constant pressure expansion valve and from the other side, the refrigerant leaves the valve to enter the evaporator.
The constructional details of the automatic expansion valve are shown in the figure below.
Automatic Expansion Valve Working Principle
- In the automatic expansion valve, the spring pressure along with the atmospheric pressure acts on the diaphragm and pushes it down. As a result, the needle also tends to move down away from the seat leading to the opening of the valve.
- The evaporator pressure pushes the diaphragm in an upward direction. Due to this, the needle tends to move in an upward direction towards the seat to close the valve.
- In the normal running condition of the plant, the valve maintains equilibrium between the evaporator pressure and the spring pressure and maintains a certain opening of the valve to allow the flow of refrigerant through it.
- The automatic expansion valve maintains the pressure inside the evaporator constant and automatically as per the setting of the spring pressure.
- When the refrigeration plant with the constant pressure valve is stopped, a certain amount of the refrigerant remains inside the evaporator and creates pressure inside the evaporator. This pressure acts against the diaphragm and keeps the valve closed. When the refrigeration plant is started again, the evaporator pressure reduces and the constant pressure expansion valve opens again.
Automatic Expansion Valve Features
- The automatic expansion valve Operates with prefixed constant pressure in the evaporator.
- It only has the bellows which is pressure operated.
- This is the only type that can be used in any machine with any refrigerant where there is a constant cooling requirement.
- When cooling decreases, pressure in the evaporator decreases. But as it has to maintain constant pressure in the evaporator, it will open more and supply more liquid refrigerant to the evaporator. Finally, it will result in sending liquid refrigerant to the compressor. The compressor will be broken as all liquids are incompressible.
- When cooling increases, pressure in the evaporator increases. But as it has to maintain constant pressure in the evaporator, the valve will open less and supply less liquid refrigerant to the evaporator. More heat is not picked by the less flow of refrigerant and hence there will be an unbalance.
- Its construction is simple.
- It is used in small cooling plants.
- It is cheap.
Automatic Expansion Valve Advantages
The automatic expansion valve provides constant pressure. This makes it easier to adjust once it has been installed when compared to other valve options. The consistent pressure also makes the compressor more efficient because it reduces the surface area and use of lower-capacity compressors.
Automatic expansion valves are also better at preventing coil freeze because it maintains a higher suction pressure at low load conditions. They also make superheat adjustments easier because the pressure the valve operates at can be adjusted after installation.
Automatic Expansion Valve Disadvantages
The main aim of the automatic expansion valve is to maintain constant pressure inside the evaporator no matter what the refrigeration load inside the evaporator is. When the load on the evaporator is high it won’t allow more flow of the refrigerant as per the requirement. Similarly, when the load is lesser, it won’t allow a reduction of the flow of the refrigerant as per the requirement. Thus the automatic expansion valve does not allow the control of the flow of the refrigerant through it which is very important for the efficient operation of the refrigeration plant.
Automatic Expansion Valve Application
The automatic expansion valves are used wherever a constant temperature is required, for instance, milk chilling units and water coolers.
They are also used in home freezers and small commercial refrigeration systems where hermetic compressors are used.
Now that you know the answer to the question of what is automatic expansion valve, how about sharing your thoughts and comments on the subject with us? Comment below and let us know what you think! And if you have any questions about the capillary tubes, sign up on Linquip right now and we’ll help you in the blink of an eye!
Which Pressures Use an Automatic Expansion Valve?
The passage of high-pressure liquid to the low-pressure evaporator is controlled by the expansion valve. The thermostatic and electrical forms of direct expansion circuits are the most common. With the help of illustrations, the thermostatic functioning of both internal and external equalization is described.
Pulse width modulation and continuous modulation are the two types of electronic modulation. Capillary tubes and restrictors are two other types of fixed orifice devices found in small systems. A float valve can regulate the flow of liquid into a flooded evaporator. This might be either high or low pressure. Low-pressure receiver circuits employ low-pressure types. Other level controllers are discussed briefly.
Buy Equipment or Ask for a Service
By using Linquip RFQ Service, you can expect to receive quotations from various suppliers across multiple industries and regions.
Click Here to Request a Quotation From Suppliers and Service Providers
Download What is Automatic Expansion Valve PDF
Read More on Linquip
- Pinch Valve Manufacturers
- Ball Valve Manufacturers
- Butterfly Valve Manufacturers
- Check Valve Manufacturers
- Valve Manufacturers
- The 10 Best Water Shut off Valves of 2022
- Ball Valve Suppliers and Companies in United States
- Check Valve Suppliers and Companies in United States
- Gate Valve Suppliers and Companies in United States
- Seat Valve Suppliers and Companies
- What is Check Valve
- What is Control Valve
- What is Diaphragm Valve
- What is Flap Valve
- What is Float Valve
- Easy Intro to Electronic Expansion Valve
- Types of Expansion Valves: an Easy to Understand Guide
- Thermal Expansion Valves: Everything You Need To Know
- Control Valve Types 101: Different Classifications, Advantage and Disadvantages
- Ball Valve Types and Their Uses
- Angle Valve: The Most Essential Tips of Features, Functions & Applications
- What is Drain Valve? Working Principle, Types & Applications
- What are Coaxial Valves? Working Principles and Type
- What is Isolation Valve? Working Principle & Types
- Backwater Valves: Working Principles & Types
- What is Block Valve? Working Principle & Types
- Solenoid Valve Installation Costs: Main Factors in 2022 + PDF
- Air Release Valve Installation Costs in 2022 + PDF
- Ball Valve Installation Costs & Repair in 2022 (Ultimate Guide)
2 thoughts on “What is Automatic Expansion Valve: A Basic Guide”
I would like to get an idea about expansion valve in proof pressure process, using water and air to reach a certain value of pressure.
Thanks for visiting our website, Kifah. You can visit our Industrial Equipment page, where you can find various pumps based on your application and demand. You can also visit our expert page and take advice from hundreds of professionals on your issue.